Outdoor Unit Control System Error. After the compressor restarts, if the same operation is repeated within 40 seconds, the compressor stops again. Evaporator fan motor error — The indoor fan speed is 0 RPM after 56 seconds from starting operation. Number of Wires and Pipes Error — When the operation command is inputted by the remote controller without check operation completion. Abnormal current value at the IPM is detected.
|Date Added:||12 June 2014|
|File Size:||33.42 Mb|
|Operating Systems:||Windows NT/2000/XP/2003/2003/7/8/10 MacOS 10/X|
|Price:||Free* [*Free Regsitration Required]|
Drivers for AVerMedia USB MPEG-2 Capture Device (E)
Serial communication error Communication Error — At Start up, evaporator and condenser are not communicating. Over Current Error — Protection stop by overcurrent generation after inverter compressor start processing com- pleted generated consecutively 10 times.
If the fujitsh operation is repeated 5 times, the compressor stops permanently. AC error codes fujitsu fujitsu halcyon inverter troubleshooting. Current transfer error — The current value during the operation after 1 minute from starting up the compressor drops to zero 0 amps.
Pipe thermistor error Indoor Heat Ex. Number of Wires and Pipes Error — When the operation command is inputted by the remote controller without check operation completion. Indoor unit fan motor 1 error High pressure switch error High Pressure Switch Error — When the pressure switch is detected open for longer than 10 seconds after the power is turned on.
Excessive high pressure protection on fkjitsu mode has been activated. Number of wires and pipes error Number of Wires and Pipes Error — When the operation command is inputted by the remote controller without check operation completion. Check-Run Unfinished — When the operation command is inputted by the remote controller without check operation completion. Discharge thermistor error Discharge Thermistor Error — When discharge pipe temperature thermistor open or short-circuit is detected at power on or while running the compressor.
Combination Unit Number Error — When the number of connecting indoor units are out of a specified rule. Check for erroneous connection or removed connector. Check thermistor resistance value.
Wired remote controller communication error Wired Remote Controller Communication Error — When the indoor unit cannot receive the signal from the. If error reappears check wiring from panel to condenser, condenser to evaporator.
Outdoor discharge pipe temperature sensor or Compressor temperature sensor short circuited. Combination Error — The outdoor unit received a signal that the applied indoor unit is that of a multi type. Pipe thermistor error Heat Ex. If the pressure switch is open for 10 seconds when the power is turned on.
Halcyon MINI-SPLITS Error Codes
Drain Pump Error — When the float switch is on for more than 3 minutes, error will trigger. Check Active Filter Module resistance values. Abnormal temperature detected -Check thermistor for open or short. Pipe Thermistor Error — Evaporator pipe thermistor e8882 an abnormal temperature. It is a non-volatile memory which keeps memorized information even if power is turned off.
After 2 minutes 20 seconds of stopped operation, the signal from the outdoor unit is received even though the main relay is off. Compressor control error Compressor Motor Control Error — If the detected rotor location is out of phase with actual rotor location more than 90 degrees, fujitsj compressor stops.
Outdoor unit main PCB error Heat Exchanger Pipe Thermistor Error — When heat exchanger temperature thermistor open or short-circuit is detected at power on or while running the compressor.
Condenser fan motor error — Abnormal current or fan motor lock error was detected. Except during defrost operation.